The air-termination rods are dimensioned according to Eurocode.
– Air-termination rod 2000 mm or tubular air-termination rod 2500 mm
– Tube Ø40 x 5 mm for mounting Ø22 / 16 mm
– Earth connection St/St with KS connector StSt for Rd 6-10 mm [lightning current carrying capability 100 kA (10/350 µsThe maximum free length relates to the distance between the rod tip and the upper support (fixing point).
For reasons of stability three supports shall be mounted. The distance between upper support and middle support must not exceed 15 cm. The lower rod holder has to be fixed in a height of ≤ 15 cm.