GENELEC Company with quality certification ISO 9001 Version 2015
Ambient conditions of reference according to ISO 8528-1:2018 normative: 1000 mbar,
25ºC, 30% relative humidity.
Prime Power (PRP):
According to ISO 8528-1:2018, Prime power is the maximum power which a
generating set is capable of delivering continuously whilst supplying a variable
electrical load when operated for an unlimited number of hours per year under the
agreed operating conditions with the maintenance intervals and procedures being
carried out as prescribed by the manufacturer. The permissible average power output
(Ppp) over 24 h of operation shall not exceed 70 % of the PRP.
Emergency Standby Power (ESP):
According to ISO 8528-1:2018, Emergency standby power is the maximum power
available during a variable electrical power sequence, under the stated operating
conditions, for which a generating set is capable of delivering in the event of a utility
power outage or under test conditions for up to 200 h of operation per year with the
maintenance intervals and procedures being carried out as prescribed by the
manufacturers. The permissible average power output over 24 h of operation shall not
exceed 70 % of the ESP
Continuous Power (COP): According to Standard ISO 8528-1:2018, this is the
maximum power available for continuous loads for unlimited running hours a year
between the maintenance times recommended by the manufacturer under the
environmental conditions established by the same.
G2 class load acceptance in accordance with ISO 8528-5:2013