Metal flat filter cell with U-section aluminium frame and double microstretched aluminium wire mesh that supports the filter fabric made up of layers of metal mesh in aluminium capped braid.
TECHNICAL CHARACTERISTICS AND LIMITS OF USE
EN ISO 16890:2016 Group ISO COARSE
(ePM1 = 1% – ePM2,5 = 2% – ePM10 = 12%)
Efficiency class (CEN EN779): G2
Average gravimetrie efficiency:65 % for 1 O mm thick filter70 % for 23 mm thick filter75 % for 48 mm thick filter
Maximum operating temperature: 200°C
Relative humidity: 100%
Initial pressure drop:5 Pa for 10 mm thick filter10 Pa for 23 mm thick filter15 Pa for 48 mm thick filter
Recommended final pressure drop: 150 Pa
Maximum pressure drop: 300 Pa
Recommended filtering velocity: 1,5 m/s
Contribute to obtain the credits of the major international rating systems for sustainable buildings:
LEED: IP, EA, MR
WELL: MATERIALS, COMMUNITY
BREEAM: MAN, WST
The filtering media is made up of layers of metal mesh in aluminium capped braid.
Prefiltration in high-efficiency filters, filtration of dry dust and oil mist, treatment of airborne fumes and greases.
Dispose of the product by separating the metal part from the filtering part. The CER code for disposal of the metal part is 120101.
Warning: declare whether