Should the monitored current exceed the set point level Imax, the protector will trip
and the red LED will illuminate indicating the fault condition. During the time delay
period the red LED will flash for the set time (t) before the relay energises output
relay contacts. The protector will automatically reset once the monitored current
falls below the set point level Imax plus the differential (internally pre-set 1%)
causing the red LED to extinguish and the relay to release without time delay.