Metal flat filter cell with U-section AISI 304 stainless steel frame and double microstretched AISI 304 stainless steel wire mesh that supports the filter fabric composed of layers of pleated microstretched mesh in AISI 304 stainless steel.
TECHNICAL CHARACTERISTICS AND LIMITS OF USE
EN ISO 16890:2016 Group ISO COARSE
(ePM1 = 1% – ePM2,5 = 2% – ePM10 = 12%)
Efficiency class (CEN EN779): G2
Average gravimetrie efficiency:65 % for 1 O mm thick filter70 % for 23 mm thick filter75 % for 48 mm thick filter
Maximum operating temperature: 350°c
Relative humidity: 100 %
Initial pressure drop:10 Pa for 10 mm thick filter20 Pa for 23 mm thick filter30 Pa for 48 mm thick filter
Recommended final pressure drop: 150 Pa
Maximum pressure drop: 300 Pa
Recommended filtering velocity: 1-1,5 m/s
Contribute to obtain the credits of the major international rating systems for sustainable buildings:
LEED: IP, EA, MR
WELL: MATERIALS, COMMUNITY
BREEAM: MAN, WST
The filtering media is composed of layers of pleated microstretched mesh in AISI 304 stainless steel.
Prefiltration of high-efficiency filters, filtration of dry dust and oil mist, treatment of airborne fumes and greases.
Dispose of the product by separating the metal part from the filtering part. The CER code tor disposal of the metal part is 120101.
Warning: declare whether the filter to be disposed of contains toxic substances.